New research supported by ASHRAE indicates that non-chemical devices (NCD) marketed to control the growth of biological agents, such as Legionella in cooling towers, may not materially reduce biological growth.
Research project No. 1361, Biological Control in Cooling Towers Using Non-Chemical Water Treatment Devices, a two year project recently completed by Dr. Radisav Vidic at the University of Pittsburgh, evaluated five non-chemical devices using different technologies to control biological activity in a model cooling tower system. The devices studied included a hydrodynamic cavitation device, pulsed and static electric field devices, an ultrasonic device and a magnetic device.
In Vidic’s research, none of the non-chemical devices measurably reduced planktonic or sessile microbial populations in comparison to no-treatment tests and to a conventional chemical microbial control treatment protocol. The findings appear to be inconsistent with previous research by non-chemical device manufacturers and some independent researchers on some of the same devices tested in the ASHRAE study. Those other studies reported measurable degrees of biological control within the parameters of testing conducted.
“These results suggest that equipment operators, building owners, and engineers should consider taking more frequent water sample tests for their systems that rely on NCDs for biological control. If the testing shows an issue, one possible measure is to add chemical treatment capability to their system to prevent a potential health hazard from developing until additional research and field testing can resolve this question,” according to Vidic.
The study results are still subject to final approval by the sponsoring technical committee, TC 3.6 – Water Treatment. For notice of when the report is available, please contact Mike Vaughn, manager of research and technical services at ASHRAE.
You might like:
- Lighting Maintenance: LED Lighting Retrofits
- Friday Funny: The Dirty Truth About Public Bathrooms
- Friday Funny: Housekeeping Olympic Games
- Cyber Security For Buildings
- Services & Maintenance: Key Pest Control Concerns For Facilities
- Site Security: Background Checks
- Hotel Case Study: A Vision By The Sea
- FM Issue: Power Protection For IoT Connection
- Texas Water Dashboard App From USGS
- Employee Engagement: Impact Of Workplace Design
- LED Innovation For Warehouse Facility
- Workplace Design: Four Trends
- Marriage Of Mobility And Facility Security
- 4 Keys To Improve Energy Efficiency Projects
- New York Offers Commercial Buildings $36M To Cut Energy Costs