ASHRAE Standard On Legionellosis Open For Comment
A proposed standard practice that specifies requirements to prevent legionellosis associated with building water systems is currently open for public review from ASHRAE. The ASHRAE Standard 188P, Prevention of Legionellosis Associated with Building Water Systems, is intended to address the “what” of controlling the spread of legionellosis. The standard helps facility managers/owners understand how to apply the available information on Legionella effectively in order to prevent cases of legionellosis associated with building water systems.
The bacterium Legionella can lead to a very serious form of pneumonia, referred to as Legionnaires’ disease, or Pontiac fever, which is a less severe form of the disease. There are many thousands of cases every year in the U.S. Essentially all cases of legionellosis are the result of exposure to Legionella associated with building water systems.
Read TFM‘s June 2011 coverage of Standard 188P in “The HVAC Factor” column here.
“We know how to analyze and control this hazard,” Bill McCoy, chair of the Standard 188P committee, said. “We need a standardized practice to specify for facility managers/owners exactly what to do in their facilities to control the hazard in a systematic and scientifically defensible way.”
The proposed standard underwent an earlier public review in November 2010 and is currently open for a second public review until July 25. Since the standard’s first public review, Section 8.1 on potable water has been rewritten. Originally, the section included several system design specifications; however, those design oriented specifications were eliminated because Standard 188P is intended to be a practices standard, rather than a design standard. The newly revised Section 8 clarifies this aspect.
Compliance with the standard requires facility managers/owners to formally take responsibility for controlling Legionella in their building water systems, while at the same time acts as a defense against accusations of negligence in those cases which are caused by the hazard from unknown sources.
Standard 188P also covers the potable water system in buildings, which are not treated as often as cooling towers, and will hold facility managers/owners accountable for properly managing the entire building water system both potable and utility water.
The standard differs from ASHRAE Guideline 12, Minimizing the Risk of Legionellosis Associated with Building Water Systems, in that while the guideline gives recommendations about how to treat various building water systems, the standard specifies the practice of exactly what must be done with all those recommendations. “The standard and the guideline are, therefore, complementary,” McCoy said.
You might like:
- The Internet Of Things And Water Management
- Look, Listen, And Learn To Find Leaks
- Top 10 States Ranked in Energy Efficiency Scorecard
- Green Buildings Improve Cognitive Function
- Facility Professionals Play Key Role In Strategic Workplace Decisions
- Webinar: Cleaner Facilities & Flu Protection
- Survey Provides Insight To Energy Management Decisions
- Question of the Week: How Do You Support Productivity In Your Facilities?
- Friday Funny: 10 Worst Cities For A Zombie Apocalypse
- Did You Miss “The Impact Of Using Defendable Data To Assess & Budget For The Future” Webinar?
- Did You Miss The “Smart Buildings, Internet of Things and What it all Means for Your Career” Webinar?
- Question Of The Week: HVAC Coil Cleaning Methods?
- China Wins Its First Emporis Skyscraper Award
- Motorized Shades Reflect Well On LEED Gold HQ
- Channel Spotlight: Commercial Roofing By Duro-Last Roofing, Inc.