By B. Kevin Folsom, CEP
Published in the November 2012 issue of Today’s Facility Manager
Q How often do you recommend replacing the belts in roof fans? We have a contract with a company, and when asked the same question during a recent checkup, the technician said they usually replace on an “as needed” basis. But from my experience I think once a year is a safer baseline. I am not comfortable with the idea of trying to stretch them too long, especially since they are not that expensive. And since the equipment is on the roof, it’s fairly easy to get there. Additionally, how often should the ventilation system be cleaned?
A I would closely scrutinize the condition of a belt prior to keeping it in service more than one year. Sometimes the larger belts in controlled environments may last several years or more. Since these oftentimes require special equipment to realign properly the cost can be more than desired to simply replace on an annual basis.
However, roof fan belts are a different story. These are exposed to the most extreme conditions, are small, and are easy to replace. The technician should remove the shroud to inspect them carefully, so they might as well replace the inexpensive belt. If you run to fail on these, you could be exposing occupants to accumulating restroom odors and increasing your reactive maintenance.
Regarding your second question, cleaning the ventilation system is based on several factors: proper filter maintenance, occupancy, and outside air quality. Ducts that are lined on the interior with porous insulation are limited with cleaning. The best way to determine cleaning frequency is to look in the ducts once per year.
Also inspect the air registers where dust may be collecting. Pay careful attention to black dust. This can often be mold and should be tested by an environmental consultant prior to disturbing. Even if there are no dangerous strains of mold present, people often have allergies to mold. You need to determine what it is prior to cleaning. I would advise cleaning any type of mold when occupants are not in the area.
You might like:
- Four Types Of Concrete Damage And How To Address Them
- Rise Of IoT Prompts Facility Professionals To Invest In Analytics
- 4 Ways To Avoid LED Lighting Failure
- Facility Management Critical To Infection Control
- Question Of The Week: What Best Practice Boosts Your Bottom Line?
- Friday Funny: The Dirty Truth About Public Bathrooms
- New Vikings Football Stadium First In U.S. With Transparent Roof
- Look, Listen, And Learn To Find Leaks
- Best Practices For Data Center Management
- FM Alert: OSHA Offering $4.6M In Safety And Health Training Grants
- Applying Lean Principles To Facility Cleaning Programs
- Energy Upgrades And Renovations: What To Know About Windows
- Technology, Aging Facilities Impacting Education Facility Budgets
- U.S. Employers Suffer Largest Talent Shortage In Skilled Trades
- Preventive Maintenance, Proactive Facility Management