By B. Kevin Folsom, CEP
Published in the October 2013 issue of Today’s Facility Manager (and also feature as the Question of the Week on September 30, 2013)
QI am having ongoing battles with sewer odors in several buildings. We have attacked this issue from several angles without a cost-effective total solution. I have treated drains, traps, and grease traps, and I have replaced grease traps. I have checked for air balance to ensure no negative air pressures. I have installed air emittance devices on vents. In cool weather, the odors still seem to invade two of our buildings. What am I missing? I know there may not be a silver bullet, but any suggestions are welcome.
Director of Maintenance
Ruidoso Municipal Schools
AThanks for writing, Lenny! It sounds as if you understand the basic engineering of sewer systems so I’ll avoid discussing that further. I have encountered this type of issue and it is a dreaded one! There are three more issues that you did not mention and that I have personally encountered in my career.
- If vent stacks are too short and/or too close to rooftop HVAC units (RTU) this can be a problem. Newer RTUs have adjustable fresh air vents to provide a proper fresh air mixture; these can suck in methane emissions from the vent stack if it’s too close and/or not high enough to get proper draft to take it away from the building.
- Cracked pipes in the wall are another possibility. The most cost-effective way to begin testing for this is with a plumbers smoke. The pipes are filled with a special smoke so you can visually see where the methane gas is going, or not going.
- Bad seals in the water closets and urinals. There are no P-traps behind or below water closets or urinals. If the seal is old, dried out, or shifted, you have a straight shot into the methane gas supply.
You might like:
- Four Types Of Concrete Damage And How To Address Them
- Rise Of IoT Prompts Facility Professionals To Invest In Analytics
- Facility Management Critical To Infection Control
- 4 Ways To Avoid LED Lighting Failure
- Question Of The Week: What Best Practice Boosts Your Bottom Line?
- Friday Funny: The Dirty Truth About Public Bathrooms
- New Vikings Football Stadium First In U.S. With Transparent Roof
- Look, Listen, And Learn To Find Leaks
- FM Alert: OSHA Offering $4.6M In Safety And Health Training Grants
- Best Practices For Data Center Management
- Applying Lean Principles To Facility Cleaning Programs
- Technology, Aging Facilities Impacting Education Facility Budgets
- Energy Upgrades And Renovations: What To Know About Windows
- U.S. Employers Suffer Largest Talent Shortage In Skilled Trades
- Preventive Maintenance, Proactive Facility Management